DANFOSS EKC 201 PDF
FFT10 interface or RS interface. For. For. EKC EKC For. For .. Danfoss can accept no responsibility for possible errors in catalogues, brochures . Introduction. Features. EKC (for panel mounting) and EKC EKC and are used for. • temperature Danfoss Pt sensors are supplied with . Danfoss EKC – Download as PDF File .pdf), Text File .txt) or read online.
|Published (Last):||3 December 2004|
|PDF File Size:||2.77 Mb|
|ePub File Size:||17.85 Mb|
|Price:||Free* [*Free Regsitration Required]|
When there is an alarm, the alarm relay will be activated for two minutes. If the controller is provided with an alarm relay, it will also be activated. Power on Room temp. All alarms are indicated by the three LEDs flashing at once.
It will collect temperature values, and it will receive alarms. Afterwards the controller is capable by itself to calculate the average value of previous cut-in times. The temperature value is set. These settings can only be made when a data communication module has been mounted in the controller and the installation of the data communication cable has been concluded.
This means that the gateway with address in the system will have its alarm relay output activated for two minutes. If SPST is cut out, alarm signalling starts and the fan is stopped, cf.
Normal operation or alarm Unknown codes and danfss Change Power off Room temp. The display shows the actual room temperature, but by activating the keys the display changes To the set or the actual temperature of the defrost sensor. Shor tcircuited defrost sensor E5 Def. The gateway can now be connected to a modem. The controllers are subsequently connected with a two-core cable.
Controller for temperature control – EKC 201 and EKC 301 Manual
ON, you reinstate ek factor y-set values Factory setting If you need to reset the controller and reinstate the factor y-set values, do the following: OFF or you set an inter val. During defrost the defrost relay will be cut in.
Danfoss Pt sensors are supplied with the controller: Contact Now Click here to send inquiry. High quality, best price!!
Danfoss Electronic Controller (EKC EKC ) –
Gold Member Since The value is set in K. Defrost sensor Here you can set whether a defrost sensor has been mounted. If not, you may cancel the function by means of setting OFF. With these settings it will only be possible to set the reference between the two values. Other code numbers have customized settings.
The function is fur thermore only relevant if you have chosen defrost with interval star t fkc Change Code Re-establish all factory settings Change Room temp.
Just push the two buttons simultaneously, and you will be able to change the temperature reference when the display responds by flashing. Push one of the buttons and select the danfsos value 5. It will cut out again when the temperature drops to the set reference value. When the time for door alarm A04 expires, a failsafe function will enter into force compressor and fan will be star ted.
Factory setting If you need to return to the factory-set values, it can be done in this way: Set it in pos OFF if you star t the defrost by means dafnoss input DI or if you mount a real-time Module danflss the controller. Easy to re-establish factory setting. When there is an alarm from one of the controllers, the gateway will via the modem call up the service company. Fitting the EKC controller with a plug-in module for communication gives access to all parameters of the controller. The time when water drips off the evaporator.
Time-controlled hot gas defrost. Buttons If you want to change a setting, the two buttons will give you a higher or lower value depending on which button you push.
A door switch is connected and the controller will register when the DI input is open. Alarm settings Alarm Settings The controller can give alarm in various situations.